Industry: Water Waste Treatment
Plant: Louth Storm Water Tank - AWS
Description: Flood control system to store, storm waste water and then return, to the Treatment Works during, stabilised conditions.
Scope of Work
Design, manufacture, test, install and commission Motor Control Centre incorporating Form 4 Board and ASTA certified busbar system.
The MCC consists of multiple sections for mains Incoming, Control and Telemetry.
Services Distribution, Return Pump starters (2 off), Storm Pump starters (3 off), Blower starters (2 off), Booster pump starter and Mobile Generator Incomer section.
Located in the Control section are two Milltronics Hydro-ranger Ultrasonic level detectors, used for tank level indication and pump start/stop control.
Telemetry system transfers control and indication signals between main Treatment works and Storm Water works.
Major Components used:
Form 4 MCC Board
Incomer and generator 160A Switch-Fuses, interlocked with Castell Key System
Milltronics Hydro-ranger Ultrasonic level detection
Return Pump D.O.L. starters 5.9KW
Storm Pump Star/Delta starters 13.5KW
MCC is suitable for a safe area environment, sited in equipment room where ingress protection IP54 is required.
Design ambient temperature is based on typical U.K. variations with room ventilation fans and heaters installed to moderate extreme variations.